(1) Check the stainless steel submersible pump and pipe and the combination of the loose phenomenon. Rotate stainless steel pump with hand, see if the stainless steel submersible pump is flexible.
(2) Adding bearing lubricating oil to bearing body, observing oil position should be in the center line of oil standard, lubricating oil should be replaced or replenished in time.
(3) Unscrew the stainless steel submersible pump body of the water diversion screw plug, pouring water (or lead slurry).
(4) The gate valve and the outlet pressure gauge and the import vacuum table of the outlet road are closed.
(5) Point motor, see if the motor steering is correct.
(6) Start the motor, when the stainless steel submersible pump normal operation, open the export pressure gauge and import vacuum pump, depending on the display of appropriate pressure, gradually hit the gate valve, and check the motor load.
(7) As far as possible to control the flow of stainless steel submersible pump and head in the range indicated on the sign, in order to ensure that stainless steel submersible pump at the highest efficiency point of operation, to obtain the maximum energy-saving effect. Import Pump Valve
(8) Stainless steel submersible pump In the process of operation, the bearing temperature can not exceed the ambient temperature of 35C, the maximum temperature should not exceed 80C.